| Return to index
Duct heater controller equipment shall be accessible with the disconnecting means installed at or within sight from the controller.
EXCEPTION: The disconnecting means shall be arranged to be locked in the "open" position if it is not within sight of the controller. A distance of 50 feet shall be considered as equivalent to being out of sight.
(Title 24, Part 3, Section 424-65.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).