|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
Duct heater controller equipment shall be accessible with the disconnecting means installed at or within sight from the controller.
EXCEPTION: The disconnecting means shall be arranged to be locked in the "open" position if it is not within sight of the controller. A distance of 50 feet shall be considered as equivalent to being out of sight.
(Title 24, Part 3, Section 424-65.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
Go Back to Article 53 Table of Contents