| Return to index
If a switch or circuit breaker serves as the disconnecting means for a stationary or fixed motor-driven appliance of more than 1/8 horsepower, it shall be located within sight from the motor controller and shall comply with the disconnecting means specified in Article 56.
(Title 24, Part 3, Section 422-26.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).