|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
If a switch or circuit breaker serves as the disconnecting means for a stationary or fixed motor-driven appliance of more than 1/8 horsepower, it shall be located within sight from the motor controller and shall comply with the disconnecting means specified in Article 56.
(Title 24, Part 3, Section 422-26.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
Go Back to Article 52 Table of Contents