|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
CONTROL AND PROTECTION OF APPLIANCES
(a) For fixed appliances rated at not over 300 volt amperes or 1/8 hp., the branch circuit overcurrent device shall be permitted to serve as the disconnecting means.
(b) For fixed appliances of greater rating the branch circuit switch or circuit breaker shall be permitted to serve as the disconnecting means where readily accessible to the user of the appliance.
(Title 24, Part 3, Section 422-21.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment of subsection (b) filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
Go Back to Article 52 Table of Contents