|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
(a) Grounding Type.
Receptacles shall be of the grounding type as prescribed in Article 6.
(b) Skirted Plugs.
Attachment plugs or other connectors supplying equipment at more than 300 volts shall be of the skirted type.
Exception: Plugs or connectors so designed that the arc will be confined within the body or case of the device shall be acceptable.
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. New section filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
2. Amendment of section and Note filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code 142.3(a)(3) (Register 2008, No. 19).
Go Back to Article 51 Table of Contents