| Return to index
(a) Single-throw knife switches and switches with butt contacts shall be so connected that the blades are deenergized when the switch is in the open position.
(b) For installations built on or after May 5, 2008 single-throw knife switches, molded-case switches, switches with butt contacts, and circuit breakers used as switches shall be connected so that the terminals supplying the load are deenergized when the switch is in the open position.
Exception: Blades and terminals supplying the load of a switch may be energized when the switch is in the open position where the switch is connected to circuits or equipment inherently capable of providing a backfeed source of power. For such installations, a permanent sign shall be installed on the switch enclosure or immediately adjacent to open switches that read, "WARNING-- LOAD SIDE TERMINALS MAY BE ENERGIZED BY BACKFEED."
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment deleting subsection (a) designation only filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
3. Amendment of section heading, section and Note filed 5-5-2008; operative 5- 5-2008. Submitted to OAL for printing only pursuant to Labor Code142.3(a)(3) (Register 2008, No. 19).
Go Back to Article 47 Table of Contents