| Return to index
(a) All pull boxes, junction boxes, and fittings shall be provided with covers identified for the purpose. If metal covers are used, they shall be grounded. In completed installations, each outlet box shall have a cover, faceplate, or fixture canopy. Covers of outlet boxes having holes through which flexible cord pendants pass shall be provided with bushings designed for the purpose or shall have smooth, well-rounded surfaces on which the cords may bear.
(b) Where a fixture canopy or pan is used, any combustible wall or ceiling finish exposed between the edge of the canopy or pan and the outlet box shall be covered with noncombustible material.
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. New section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code 142.3(a)(3) (Register 2008, No. 19).
Go Back to Article 45 Table of Contents