| Return to index
(a) Material. Equipment bonding jumpers shall be of copper or other corrosion-resistant material.
(b) Attachment. Equipment bonding jumpers shall be attached in the manner specified by the applicable provisions of Section 2395.113 for circuits and equipment.
(c) Installation. The equipment bonding jumper shall be permitted to be installed inside or outside of a raceway or enclosure. Where installed on the outside, the length of the equipment bonding jumper shall not exceed six (6) feet and shall be routed with the raceway or enclosure.
(Title 24, Part 3, Section 250-79(a), (b) and (e).)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. New section filed 3-20-79; effective thirtieth day thereafter (Register 79, No. 12).
2. Editorial correction filed 11-2-83 (Register 83, No. 45).
3. Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
Go Back to Article 11 Table of Contents