|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
Regardless of the voltage of the electrical system, the electrical continuity of metal noncurrent-carrying parts of equipment, raceways, and other enclosures in any hazardous location as defined in Article 59 of these Orders shall be assured by any of the methods specified for services that are approved for the wiring method used.
(Title 24, Part 3, Section 250-78.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
Go Back to Article 11 Table of Contents