|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
The metal noncurrent-carrying parts of equipment indicated in (a), (b), and (c) below shall be effectively bonded together:
(a) Service raceways cable trays or service cable armor or sheath;
(b) All service equipment enclosures containing service-entrance conductors, including meter fittings, boxes, or the like, interposed in the service raceway or armor;
(c) Any metallic raceway or armor enclosing a grounding electrode conductor.
(Title 24, Part 3, Section 250-71(a).)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
Go Back to Article 11 Table of Contents