| Return to index
The metal noncurrent-carrying parts of equipment indicated in (a), (b), and (c) below shall be effectively bonded together:
(a) Service raceways cable trays or service cable armor or sheath;
(b) All service equipment enclosures containing service-entrance conductors, including meter fittings, boxes, or the like, interposed in the service raceway or armor;
(c) Any metallic raceway or armor enclosing a grounding electrode conductor.
(Title 24, Part 3, Section 250-71(a).)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
Go Back to Article 11 Table of Contents