|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
Where an AC system is connected to a grounding electrode in or at a building as specified in Section 2395.23, the same electrode shall be used to ground conductor enclosures and equipment in or on that building.
NOTE: Two or more electrodes that are effectively bonded together shall be considered as a single electrode in this sense.
(Title 24, Part 3, Section 250-54).
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
Go Back to Article 11 Table of Contents