| Return to index
Where an AC system is connected to a grounding electrode in or at a building as specified in Section 2395.23, the same electrode shall be used to ground conductor enclosures and equipment in or on that building.
NOTE: Two or more electrodes that are effectively bonded together shall be considered as a single electrode in this sense.
(Title 24, Part 3, Section 250-54).
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).