|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
For AC premises wiring systems the conductor required to be grounded by Section 2395.5 shall be as follows:
(a) One conductor of a single-phase, two-wire system shall be grounded;
(b) The neutral conductor of a single-phase, three-wire system shall be grounded;
(c) The common conductor of a multiphase system having one wire common to all phases shall be grounded;
(d) One phase conductor of a multiphase system where one phase is grounded shall be grounded; and
(e) The neutral conductor of a multiphase system in which one phase is used as a neutral conductor shall be grounded.
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Repealer and new section filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
3. Amendment of section and Note filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code 142.3(a)(3) (Register 2008, No. 19).
Go Back to Article 11 Table of Contents