|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
Conductors and equipment shall be protected from overcurrent in accordance with their ability to safely conduct current.
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. Repealer of Article 10 (Sections 2390.1-2390.83, not consecutive) and new Article 10 (Sections 2390.1-2390.41, not consecutive) filed 11-16-79; effective thirtieth day thereafter (Register 79, No. 46).
2. Editorial correction filed 11-2-83 (Register 83, No. 45).
3. Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
4. Amendment of section and Note filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code 142.3(a)(3) (Register 2008, No. 19).
Go Back to Article 10 Table of Contents