| Return to index
Conductors on poles shall have a separation of not less than 1 foot (305 mm) where not placed on racks or brackets. Conductors supported on poles shall provide a horizontal climbing space not less than the following:
(a) Power conductors below communication conductors -30 in. (762 mm);
(b) Power conductors alone or above communication conductors:
(1) 300 volts or less -24 in. (610 mm),
(2) Over 300 volts -30 in. (762 mm);
(c) Communication conductors below power conductors -same as power conductors; and
(d) Communications conductors alone -no requirement.
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. New section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code 142.3(a)(3) (Register 2008, No. 19). For prior history, see Register 79, No. 32.
Go Back to Article 8 Table of Contents