|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
Conductors on poles shall have a separation of not less than 1 foot (305 mm) where not placed on racks or brackets. Conductors supported on poles shall provide a horizontal climbing space not less than the following:
(a) Power conductors below communication conductors -30 in. (762 mm);
(b) Power conductors alone or above communication conductors:
(1) 300 volts or less -24 in. (610 mm),
(2) Over 300 volts -30 in. (762 mm);
(c) Communication conductors below power conductors -same as power conductors; and
(d) Communications conductors alone -no requirement.
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. New section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code 142.3(a)(3) (Register 2008, No. 19). For prior history, see Register 79, No. 32.
Go Back to Article 8 Table of Contents