| Return to index
(a) Receptacles installed on 15- and 20-ampere branch circuits shall be of the grounding type except as permitted for replacement receptacles in subsection (d) of this section. Grounding-type receptacles shall be installed only on circuits of the voltage class and current for which they are rated, except as provided in Table 2360.4(b)(2) and Table 2360.4(b)(3).
(b) Receptacles and cord connectors having grounding contacts shall have those contacts effectively grounded except for receptacles mounted on portable and vehicle-mounted generators in accordance with Section 2395.6 of these Orders and replacement receptacles installed in accordance with subsection (d) of this section.
(c) The grounding contacts of receptacles and cord connectors shall be grounded by connection to the equipment grounding conductor of the circuit supplying the receptacle or cord connector. The branch circuit wiring method shall include or provide an equipment grounding conductor to which the grounding contacts of the receptacle or cord connector shall be connected.
(d) Replacement of receptacles shall comply with the following requirements:
(1) Where a grounding means exists in the receptacle enclosure or a grounding conductor is installed, grounding-type receptacles shall be used and shall be connected to the grounding means or conductor;
(2) Ground-fault circuit-interrupter protected receptacles shall be provided where replacements are made at receptacle outlets that are required to be so protected elsewhere in these Orders; and
(3) Where a grounding means does not exist in the receptacle enclosure, the installation shall comply with one of the following provisions:
(A) A nongrounding-type receptacle may be replaced with another nongrounding-type receptacle; or
(B) A nongrounding-type receptacle may be replaced with a ground-fault circuit-interrupter-type of receptacle that is marked "No Equipment Ground;" an equipment grounding conductor shall not be connected from the ground-fault circuit-interrupter-type receptacle to any outlet supplied from the ground-fault circuit-interrupter receptacle; or
(C) A nongrounding-type receptacle may be replaced with a grounding-type receptacle where supplied through a ground-fault circuit-interrupter; the replacement receptacle shall be marked "GFCI Protected" and "No Equipment Ground;" an equipment grounding conductor shall not be connected to such grounding-type receptacles.
(e) Receptacles connected to circuits having different voltages, frequencies, or types of current (ac or dc) on the same premises shall be of such design that the attachment plugs used on these circuits are not interchangeable.
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. New section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code 142.3(a)(3) (Register 2008, No. 19).