|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
For installations built on or after May 5, 2008 where more than one nominal voltage system exists in a building containing multiwire branch circuits, each ungrounded conductor of a multiwire branch circuit, where accessible, shall be identified by phase and system. The means of identification shall be permanently posted at each branch-circuit panelboard.
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. New article 6 (sections 2360.1-2360.5) and section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code142.3(a)(3) (Register 2008, No. 19). For prior history of article 6, see Register 79, No. 32.
Go Back to Article 8 Table of Contents