| Return to index
Electric equipment shall be installed in a neat and workmanlike manner.
(a) Unused openings in boxes, raceways, auxiliary gutters, cabinets, equipment cases, or housings shall be effectively closed to afford protection substantially equivalent to the wall of the equipment.
(b) Conductors shall be racked to provide ready and safe access in underground and subsurface enclosures that persons enter for installation and maintenance.
(c) Internal parts of electrical equipment, including busbars, wiring terminals, insulators, and other surfaces, shall not be damaged or contaminated by foreign materials such as paint, plaster, cleaners, abrasives, or corrosive residues.
(d) There shall be no damaged parts that may adversely affect safe operation or mechanical strength of the equipment, such as parts that are broken, bent, cut, or deteriorated by corrosion, chemical action, or overheating.
Note: Authority cited: Section 142.3, Labor Code. Reference Section 142.3, Labor Code.
1. New section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code 142.3(a) (3) (Register 2008, No. 19). For prior history, see Register 79, No. 12.