|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
(a) Suitable temporary barriers, or barricades, shall be installed when access to opened enclosures containing exposed energized electrical equipment is not under the control of an authorized person.
(b) Conductive measuring tapes, ropes or similar measuring devices shall not be used when working on or near exposed energized conductors or parts of equipment.
(c) Conductive fish tapes shall not be used in raceways entering enclosures containing exposed energized parts unless such parts are isolated by suitable barriers.
(d) Prior to climbing poles or other elevated structures supporting overhead electrical lines or equipment, an inspection shall be made to assure that such poles or structures are in safe condition for the work to be performed. Where poles or structures are determined to be unsafe for climbing, they shall not be climbed until made safe by guying, bracing or other adequate means.
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. Editorial correction adding NOTE filed 11-2-83 (Register 83, No. 45).
2. Amendment of section heading and new subsection (d) filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
Go Back to Article 3 Table of Contents