|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
Regulators that reduce the vapor pressure of fuel gas to not more than 20 psi are required for all installations within structures or confined spaces unless the burner or appliance specifically requires a higher pressure and equivalent safety is provided. The use of regulators or automatic pressure-reducing valves shall be limited to the pressures and the types of gases for which they were designed. Regulators are required for installations where a fuel gas hose is between fuel source and burner.
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. New NOTE filed 1-5-87; effective thirtieth day thereafter (Register 87, No. 2).
Go Back to Article 32 Table of Contents