|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
(a) The ends of all tubes, suspension tubes, and nipples of water-tube boilers and superheaters may be seal-welded in accordance with the provisions of paragraph PWT-11 of the Code.
(b) Seal-welding of circumferential joints is permissible, provided the seam is calked first and made tight under hydrostatic pressure equal to the working pressure.
(c) The ends of fire tubes may be seal-welded provided the thickness of the tube is at least seventy-five percent (75%) of its original thickness, and the tubes are first rolled and beaded and found tight under hydrostatic pressure at least equal to the working pressure. The throat of the weld shall not exceed three-sixteenths inch (3/16").
1. Amendment filed 11-2-66; effective thirtieth day thereafter (Register 66, No. 38). Approved by State Building Standards Commission.
Go Back to Article 7 Table of Contents