|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
(a) Combustible liquids and gases shall be stored at least 100 feet from the following:
(1) Mine openings
(2) Buildings and snow sheds connected to mine openings
(3) Ventilation fan houses
(4) Hoist houses
(5) Explosive magazines
The storage place shall be located where contents of leaking containers cannot run over the surface to any point within 100 feet of the above-mentioned places and structures.
NOTE: Certain petroleum gases, such as butane and propane, are compressed to liquid form in pressure tanks. When a tank containing liquefied petroleum gases leaks or is ruptured, the contents vaporize in the atmosphere. These vapors are heavier than air and will flow downhill over the surface of the ground much like water until the vapors are diffused. For this reason tanks containing liquefied petroleum gases must be stored at locations which are in compliance with the provisions of this section.
Go Back to the Mine Safety Orders, Article 22 Table of Contents