Suitable fire-control devices, such as small hose or portable fire extinguishers, shall be available to locations where fires are likely to occur. Additional fire-control equipment may be required where a tank of more than 50,000 gallons individual capacity contains Category 1 or 2 flammable liquids, or Category 3 flammable liquids with a flashpoint below 100oF (37.8oC), and where an unusual exposure hazard exists from surrounding property. Such additional fire-control equipment shall be sufficient to extinguish a fire in the largest tank. The design and amount of such equipment shall be in accordance with approved engineering standards.
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. Amendment filed 7-16-76; effective thirtieth day thereafter (Register 76, No. 29).
2. Amendment of section and new Note filed 5-5-2014; operative 5-6-2014 pursuant to Government Code section 11343.4(b)(3) (Register 2014, No. 19).
This database is current through 6/6/14 Register 2014, No. 23