|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.
Subchapter 7. General Industry Safety Orders
Group 20. Flammable Liquids, Gases and Vapors
Article 145. Tank Storage
§5600. Installation of Tanks Inside of Buildings.
(a) Location. Tanks shall not be permitted inside of buildings except as provided in Articles 142, 143, 144 or 148.
(b) Vents. Vents for tanks inside of buildings shall be as required in Sections 5592, 5593, 5594(b) and 5598 except that emergency venting by the use of weak roof seams on tanks shall not be permitted. Automatic sprinkler systems installed in an approved manner, shall be accepted as equivalent to approved water spray systems for purposes of calculating the required air flow rates for emergency vents in Section 5593(g). Except for tanks containing Class IIIB liquids, vents shall terminate outside the buildings.
(c) Vent Piping. Vent piping shall be constructed in accordance with Article 146.
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. Amendment of subsection (b) and new Note filed 7-23-2013; operative 10-1-2013 (Register 2013, No. 30).
Go Back to Article 145 Table of Contents