|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
(a) Heating equipment may be installed in the conventional manner except as provided in (b), (c), (d), or (e).
(b) Heating equipment may be installed in a special room separated from an area classified as Division 1 or Division 2 in Table FL-9 by walls having a fire-resistance rating of at least one hour and without any openings in the walls within 8 feet of the floor into an area classified as Division 1 or Division 2 in Table FL-9. This room shall not be used for combustible storage, and all air for combustion purposes shall come from outside the building.
(c) Heating equipment using gas or oil fuel may be installed in the lubrication or service room where there is no dispensing or transferring of Class I liquids provided the bottom of the combustion chamber is at least 18 inches above the floor and the heating equipment is protected from physical damage.
(d) Heating equipment using gas or oil fuel listed for use in garages may be installed in the lubrication or service room where Class I liquids are dispensed provided the equipment is installed at least 8 feet above the floor.
(e) Electrical heating equipment shall conform to Section 5574. (Title 24, T8-5575)
1. Amendment filed 7-16-76; effective thirtieth day thereafter (Register 76, No. 29).
Go Back to Article 144 Table of Contents