|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
(a) Bulk oxygen storage containers, regardless of design pressure, shall be equipped with safety relief devices as required by the ASME Code or the DOT Specifications and Regulations. (See Section 5503.)
(b) Bulk oxygen storage containers designed and constructed in accordance with a DOT Specification shall be equipped with safety relief devices as required by the DOT. See Subsection 5503(c)(2).
(c) Bulk oxygen storage containers designed and constructed in accordance with the ASME Boiler and Pressure Vessel Code, Section VIII--Unfired Pressure Vessels (1974), shall be equipped with safety relief devices meeting the provisions of Compressed Gas Association Pamphlet "Safety Relief Device Standards for Compressed Gas Storage Containers," S-1, Part 3.
(d) Insulation casings on liquid oxygen containers shall be equipped with suitable safety relief devices.
(e) All safety relief devices shall be so designed or located that moisture cannot collect and freeze in a manner which could interfere with proper operation of the device.
1. Amendment of subsection (c) filed 3-2-76; effective thirtieth day thereafter (Register 76, No. 10).
Go Back to Article 139 Table of Contents