|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
(a) Roadways and yard surfaces located below liquefied hydrogen piping, from which liquid air may drip, shall be constructed of noncombustible materials.
(b) If protective walls are provided, they shall be constructed of noncombustible materials and in accordance with the provisions of the definition of "Outdoor Location" (See Section 5415) as applicable.
(c) Electrical wiring and equipment shall comply with Sections 5489 (a) and (b).
(d) Adequate lighting shall be provided for nighttime transfer operation. (Title 24, T8-54954).
1. Amendment of subsections (b) and (c) filed 3-2-76; effective thirtieth day thereafter (Register 76, No. 10).
2. Amendment filed 7-16-76; effective thirtieth day thereafter (Register 76, No. 29).
Go Back to Article 138 Table of Contents