|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
(a) The system shall be located so that it is readily accessible to delivery equipment and to authorized personnel.
(b) Systems shall be located above ground.
(c) Systems shall not be located beneath electric power lines.
(d) Systems shall not be located close to flammable liquid piping or piping of other flammable gases.
(e) Systems near above ground flammable liquid storage shall be located on ground higher than the flammable liquid storage except when dikes, diversion curbs, grading, or separating solid walls are used to prevent accumulation of flammable liquids under the system.
Go Back to Article 138 Table of Contents