|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
Every bulk storage tank, dispensing tank, transportation tank and bulk delivery tank shall be provided with a suitable pressure gage. The pressure gage shall be installed in a special gage outlet installed permanently on the tank or tank system and having an opening not to exceed No. 54 drill size opening at the tank connection. Pressure gages for LNG vessels shall have their connection above the maximum permissible liquid level. The pressure gage shall have a dial graduated to read approximately double the operating pressure, but in no case less than 1.2 times the pressure at which the pressure relief valve is set to function.
Go Back to Article 7 Table of Contents