|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
(a) Inside generator rooms or outside generator houses shall be well ventilated with vents located at floor and ceiling levels.
(b) Heating shall be by steam, hot water, enclosed electrically heated elements or other indirect means. Heating by flames or fires shall be prohibited in outside generator houses or inside generator rooms, or in any enclosure communicating with them.
(c) All generator houses or rooms shall have natural lighting during daylight hours. Where artificial lighting is necessary, it shall be restricted to electric lamps installed in accordance with Electrical Safety Orders for hazardous locations. (Title 8, Section 2540.1 et seq.)
(d) All electrical equipment in and around an acetylene generator house, room or compartment shall be installed in accordance with Electrical Safety Orders for hazardous locations.
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. Amendment filed 7-16-76; effective thirtieth day thereafter (Register 76, No. 28).
2. Amendment filed 6-12-87; operative 7-12-87 (Register 87, No. 26).
Go Back to Article 82 Table of Contents