| Return to index
(a) If exposed to contact with electric light and power conductors, the metal sheath of aerial cables entering buildings shall be grounded or shall be interrupted close to the entrance to the building by an insulating joint or equivalent device. Where protective devices are used, they shall be grounded in an approved manner.
(b) Masts and metal structures supporting antennas shall be permanently and effectively grounded without splice or connection in the grounding conductor.
(c) Transmitters shall be enclosed in a metal frame or grill or separated from the operating space by a barrier, all metallic parts of which are effectively connected to ground. All external metal handles and controls accessible to the operating personnel shall be effectively grounded. Unpowered equipment and enclosures are considered to be grounded where connected to an attached coaxial cable with an effectively grounded metallic shield.
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. New section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code 142.3(a)(3) (Register 2008, No. 19).
Go Back to Article 87 Table of Contents