| Return to index
Portable plugging boxes shall comply with (a) through (d) below.
(a) Enclosure. The construction shall be such that no current-carrying part will be exposed.
(b) Receptacles and Overcurrent Protection. Each receptacle shall have a rating of not less than 30 amperes, and shall have overcurrent protection installed in an enclosure equipped with self-closing doors.
(c) Busbars and Terminals. Busbars shall have an ampacity equal to the sum of the ampere ratings of all the receptacles. Lugs shall be provided for the connection of the master cable.
(d) Flanged Surface Inlets. Flanged surface inlets (recessed plugs) that are used to accept the power shall be rated in amperes.
(Title 24, Part 3, Section 520-62.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
Go Back to Article 70 Table of Contents