|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
This Article covers the installation of all transformers.
Exception: No: 1: Current transformers.
Exception: No: 2: Dry-type transformers that constitute a component part of other apparatus and comply with the requirements for such apparatus.
Exception: No: 3: Transformers which are an integral part of an X-ray, high-frequency, or electrostatic-coating apparatus.
Exception: No: 4: Transformers for sign and outline lighting that comply with Article 73.
Exception: No: 5: Transformers for electric-discharge lighting that comply with Article 51.
Exception: No: 6: Transformers used for power limited fire protective signaling circuits.
Exception: No: 7: Transformers used with Class 2 and Class 3 circuits.
Exception: No: 8: Liquid-filled or dry-type transformers used for research, development, or testing, where effective arrangements are provided to safeguard unqualified persons from contacting high-voltage terminals or energized conductors.
This Article also covers the installation of transformers in hazardous locations as modified by Article 59.
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Editorial correction filed 11-3-83 (Register 83, No. 45).
3. Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
4. Amendment of section and Note filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code 142.3(a)(3) (Register 2008, No. 19).
Go Back to Article 57 Table of Contents