This information is provided free of charge by the Department of Industrial Relations
from its web site at www.dir.ca.gov. These regulations are for the
convenience of the user and no representation or warranty is made that the information
is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.
Subchapter 5. Electrical Safety Orders
Group 2. High-Voltage Electrical Safety Orders
Article 27. Transformers (Formerly Article 76)
(a) Ventilation. Adequate ventilation shall be provided to assure safe operating temperature of apparatus.
(b) Protection from Physical Damage. Transformers and attachments, such as conductors and externally mounted devices, shall be protected from physical damage by suitable barriers, guards, or location.
(c) Identification. Each transformer shall be identified by a permanent nameplate which includes the following information:
| ||(1) The word(s) "Transformer," "Voltage Regulating Transformer," or "Voltage Regulator."|| |
| ||(2) Manufacturer's name, type, and serial designation.|| |
| ||(3) Rated KVA, phases, and frequency.|| |
| ||(4) Voltage ratings and tap voltages.|| |
| ||(6) Polarity (single phase).|| |
| ||(8) Rated temperature rise in degrees centigrade.|| |
| ||(9) Identification of insulating medium.|| |
| ||(10) Amount of insulating liquid (not required for sizes 167 KVA and smaller).|| |
| ||(11) Approximate total weight (not required for sizes 25 KVA and smaller).|| |
(d) Access Openings. Access openings to transformer enclosures shall be provided with a means for locking or otherwise preventing unauthorized access.
| ||(1) A permanent, legible, and clearly visible "HIGH VOLTAGE" warning sign, having letters at least 2 inches high, shall be located on the access opening of each transformer enclosure. These signs shall read substantially as follows: "Danger-High Voltage - Keep Out."|| |
<General Materials (GM) - References, Annotations, or Tables>
| ||(2) The operating voltage of exposed live parts of transformer installations shall be indicated by signs or visible markings on the equipment or structure.|| |
| || Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code. || |
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 12-10-87; operative 1-9-88 (Register 88, No. 1).
3. Amendment of section and Note filed 4-1-2009; operative 4-1-2009. Submitted
to OAL for printing only pursuant to Labor Code section 142.3 (Register
2009, No. 14).
Go Back to Article 27 Table of Contents